14 AWG must be protected at 15A, according to NEC 240.4(D)(3). 14 AWG can't be used on a circuit with a 20A breaker. The screw terminals are the better choice if you want to put 15 Amp receptacle on a 20 Amp circuit with 12 gauge wire. You can use the side terminals.
Let's Get It Fixed!
Our virtual experts can diagnose your issue (for free!) and resolve simple problems.