I said metal gas piping needs to bebonded to the grounded conductor. Is this true? Section 250-104(b) requires the bonding of metal gas piping to the grounding system. The neutral bar is where this can be terminated.
Let's Get It Fixed!
HomeX virtual experts will assess your issue (for free!) and can resolve simple problems.