Use a screwdriver to connect the hot circuit wire to the "HOT" or "LOAD" screw terminal. The neutral circuit wire needs to be connected to the "neutRAL" screw terminal. The neutral wire should be connected to the neutral bus bar on the service panel.
Let's Get It Fixed!
HomeX virtual experts will assess your issue (for free!) and can resolve simple problems.