The pressure reading should be converted to the saturation temperature using the appropriate pressure chart. Evaporator coil super heat can be calculated by subtracting the saturation temperature from the suction line temperature.
Let's Get It Fixed!
HomeX virtual experts will assess your issue (for free!) and can resolve simple problems.