The furnace's breaker should be turned off. Find the wires that connect to the thermostat after removing the access panel. The thermostat wire should be disconnected from the G terminal. Is that correct? If you have both central heat and air, you'll need to make a jumper with an 18 AWG wire.
Let's Get It Fixed!
HomeX virtual experts will assess your issue (for free!) and can resolve simple problems.