The conductors must be 125% of the motor FLC. The overloads must not be more than 125% of the motor's current rating. You have to size the short-circuit ground-fault protection device from 150% to 300% of the motor FLC.
Let's Get It Fixed!
HomeX virtual experts will assess your issue (for free!) and can resolve simple problems.