The conductors must be 125% of the motor FLC. The overloads must not be more than 125% of the motor's current rating. The short-circuit ground-fault protection device should be between 150% and 300% of the motor FLC.
Let's Get It Fixed!
Our virtual experts can diagnose your issue (for free!) and resolve simple problems.