Use a screwdriver to connect the hot circuit wire to the "HOT" or "LOAD" screw terminal. The neutral circuit wire needs to be connected to the "neutRAL" screw terminal. The neutral wire should be connected to the neutral bus bar on the service panel.
Let's Get It Fixed!
Our virtual experts can diagnose your issue (for free!) and resolve simple problems.