If the equipment doesn't have a load neutral, the GFCI isn't needed. The pig tail white coiled wire needs to be connected to the neutral bar in order for the electronics to function. The ground bar should be connected to the ground as usual.
Let's Get It Fixed!
HomeX virtual experts will assess your issue (for free!) and can resolve simple problems.