If the equipment doesn't have a load neutral, the GFCI isn't needed. The pig tail white coiled wire needs to be connected to the neutral bar in order for the electronics to function. The ground bar should be connected to the ground as usual.
Let's Get It Fixed!
Our virtual experts can diagnose your issue (for free!) and resolve simple problems.