Check and calibrate the thermostat. As needed, clean or replace the standard 1” filter. The fan motor has a volts/amps monitor on it. Check bearings for wear. ... If accessible, inspect indoor coil. ... Take a look at the drain drain. ... The condenser coil needs to be inspected. The operating pressure of the refrigerant should be monitored.
Let's Get It Fixed!
HomeX virtual experts will assess your issue (for free!) and can resolve simple problems.