The breaker will work with or without a load neutral wire on 2P 15A to 50A. The white curly wire must still be connected to the panel neutral if there is no load neutral wire. There is no load neutral wire connection on the breaker on 2P 60A and all 3P.
Let's Get It Fixed!
Our virtual experts can diagnose your issue (for free!) and resolve simple problems.