The hot-to-neutral reading should be higher than the hot-to-ground reading. The ground isn't connected to a voltage source on the receptacle end of the ground path. The ground wire is a long test lead.
Let's Get It Fixed!
Our virtual experts can diagnose your issue (for free!) and resolve simple problems.