You need to measure neutral-ground or hot-ground. If neutral-ground is 120 V and hot-ground is less than that, then neutral and hot have been reversed. It's normal to have a neutral-ground voltage of 2 V or less under load conditions.
Let's Get It Fixed!
HomeX virtual experts will assess your issue (for free!) and can resolve simple problems.